Parameters not available in standardized GAPC LN - StrVal
For the calculation of phasors, it might be of interest to verify that there is no transient in the time window used for the calculation of the phasor. This can be done by comparing the DC and harmonic components resulting from the FFT of the time window. The corresponding thresholds can be express by StrVal of GAPC, as long as this feature is not implemented in MMXU LN.
[New parametres need to be modelled in GAPC LN. This issue refer to StrVal parameters, as explained in the attached documents by RTE.]