Report of current active setting group
To create a new INS data object in the LLN0 where SCGB is defined. A new presence condition is needed. To be included in IEC 61850-7-4 ed3.
The current active setting group cannot be sent in a report in an spontaneous way, and you can only use GetDataValues (polling) service.
Today some users define a INS data object with the setting group number, others define several SPS objects to indicate which seeting group is active.
Service tracking gives information about the current setting group, but it is not possible by GOOSE or report. If you want to raise an action on other device due to a setting group change, then you need a data object with TrgOpts d-chg in order to be able to do it.
Updated by Carlos Rodriguez del Castillo over 2 years ago
- Short Proposal changed from To create an INS to To create a new INS data object in the LLN0 where SCGB is defined. A new presence condition is needed. To be included in IEC 61850-7-4 ed3.
- Standard(s) set to IEC 61850-7-4
- Estimated Completion set to IEC 61850-7-4 edition 3