Clarifications on the local/remote concept 8/8
Annex B, Table B.1 states that "Manual Control at switch (process)" was always allowed. Isn't it the status of a control switch modelled as XCBR.LocKey="true" which releases the manual control at the switchgear? As long as this control switch is not activated, manual control is not possible. To prevent from switchgear controls other than local during this time, as long as XCBR.LocKey="true", no control issued by the IED is accepted.