Figure 15 SelOpn and SelCls are incorrect
I found an inconsistency in SelOpn and SelCls definitions between IEC 61850-7-500 Ed2 and 61850-7-4 Ed2.1. Can we discuss this during today’s meeting if time permits?
Figure 15 in 61850-7-500 shows SelOpn and SelCls with per-phase data attributes (as if it were an ACT). However, 61850-7-4 Ed2.1 defines SelOpn and SelCls as SPS. Even for single-phase control, the selection has to be per-switch. I believe this diagram needs to be updated.
Development Lead Engineer
Research and Development
Schweitzer Engineering Laboratories
901 Center Park Drive, Charlotte, NC 28217 USA | Office: (704)-504-6804
Updated by Keith Gray 3 months ago
- Status changed from New to In Progress
Michael has the correct drawing from the original work. He has updated 7-500 and will send the update to Keith. Keith will organize these updated files in the collaboration platform as we prepare to update the official version of 7-500.